Brown Daugaard posted an update 1 year, 3 months ago
Increasing the quality water involves disinfection plus purification of untreated surface and ground water.
Community Level. A public/private water treatment facility aims to generate water safe to consume and pleasant to taste, whilst making sure that there exists enough water to produce the requirements the neighborhood.
Raw, untreated water arises from an underground aquifer (via wells) or surface ponds just like a river or lake. It flows or is pumped to a treatment facility. As soon as it’s there, the river is treated beforehand to remove debris – like leaves and silt. Then it goes through a number of treatment processes, that include disinfection and filtration using chemicals or physical processes, eliminating microorganisms that induce diseases. As soon as the treatment is completed, water flows out through a system of pumps and pipes, and this can be called the distribution system.
You will find there’s slight difference of water treatment process at various places, in line with the technology in the plant and water would have to be processed, but the fundamental principles are mainly the identical.
Coagulation / Flocculation. On the coagulation state, liquid aluminium sulfate or alum, and at times polymer, lies in untreated/raw water. A combination causes tiny dirt particles in water to become fastened together or coagulated. Then, collections of dirt particles join together to make bigger, heavier particles Known as flocs – that are easily removed through filtration/settling.
Sedimentation. When water and floc particles have the treatment process, they flow into sedimentation basins where water moves slowly, letting heavy floc particles dip to the bottom. Floc collected for the lowermost area of the basin is known as sludge. This holds through pipes to achieve the drying lagoons. The sedimentation state is not contained in Direct Filtration so, the floc is removed through filtration.
Filtration. Water experiences a filter intended to remove water particles. The filters contain layers of gravel and sand, plus other cases, crushed anthracite. Filtration gathers the suspended water impurities and improves the efficacy of disinfection. Filters are cleaned often by means of backwashing.
Disinfection. Before water goes into the distribution system, it can be disinfected to be sure that bacteria that causes diseases, parasites and viruses is eliminated. Chlorine is used mainly because it a great in disinfecting and residual concentration to shield from possible biological contamination contained in it of water distribution.
More details about Sistemy vodoochistki please visit internet page: